The GRANITE™9 and GRANITE™10 are the most computationally powerful data-acquisition devices from Campbell Scientific. As an all-digital measurement and control DAQ, the GRANITE 9 is designed as the core of the data-acquisition network, integrating with all GRANITE measurement modules, including the VOLT 108, VOLT 116, TEMP 120, VWIRE 305, and CH400.Read More
The GRANITE 9 enables you to perform the following:
A complete GRANITE system installation may include the following components:
|-NOTE-||Additional specifications are listed in the GRANITE 9 Specifications.|
|Power Requirements||9.6 to 32 Vdc (voltage input)|
|Real-Time Clock Accuracy||±3 min. per year|
|Operating Temperature Range||
|Case Material||Stainless steel 304 and aluminum 6061|
|Data Storage Ports||
|Digital I/O||8 terminals (C1 to C8) configurable for digital input and output. Terminals are configurable in pairs for 5 V or 3.3 V logic for some functions.|
|Internet Protocols||Ethernet, PPP, RNDIS, ICMP/Ping, Auto-IP (APIPA), IPv4, IPv6, UDP, TCP, TLS (v1.2), DNS, DHCP, SLAAC, Telnet, HTTP(S), SFTP, FTP(S), POP3/TLS, NTP, SMTP/TLS, SNMPv3, CS I/O IP|
|Communication Protocols||CPI, EPI PakBus, PakBus Encryption, SDM, SDI-12, Modbus RTU / ASCII / TCP, DNP3, custom user definable over serial, UDP, NTCIP, NMEA 0183, I2C, SPI|
|Battery-backed SRAM for CPU Usage & Final Storage||4 MB|
|Data Storage||4 MB SRAM + 128 MB NOR flash (Storage expansion of up to 16 GB with removable microSD flash memory card.)|
|Active Current Drain, Average||
|Static Vibrating-Wire Measurements||Not supported|
21.4 x 12.0 x 5.0 cm (8.4 x 4.7 x 2.0 in.)
Additional clearance required for cables and leads.
|Weight||1.0 kg (2.2 lb)|
Please note: The following shows notable compatibility information. It is not a comprehensive list of all compatible products.
|GRANITE TEMP 120||Requires OS version 1 or greater.|
|GRANITE VOLT 108|
|GRANITE VOLT 116|
|GRANITE VWIRE 305|
This OS should only be updated via direct connection with the GRANITE 9.
This download is for the GRANITE 9 datalogger. Execution of this download places the Operating System file(.obj) on your computer. It also updates the CRBasic Editor compiler and support files.
Note/Warning: Campbell Scientific always recommends updating operating systems on site if possible. When remote updates are required, it is recommended that you implement the necessary precautions to handle unexpected OS upload complications. All datalogger settings should be retained when updated remotely. If you choose to roll back to a previous operating system, the datalogger settings will be reset to default.
Program to read 20 Hz dynamic data from two GRANITE VWIRE 305 analyzers measuring eight channels each.
Number of FAQs related to GRANITE 9: 1
The CPI bus speed is adjustable in your CRBasic data logger program. Use the CPISpeed() instruction in your CRBasic program to adjust the CPI bus bandwidth to meet the following maximum combined (total) Ethernet cable lengths: