The ENC10/12 is a weather-resistant enclosure that is 10 inches wide and 12 inches tall. This enclosure can house and protect a smaller datalogger, a power supply, and a small peripheral. Or it can house a peripheral that needs to be housed in an enclosure separate from the datalogger.Read More
The ENC10/12's backplate is prepunched with half-inch-on-center holes suitable for attaching a data logger, power supply, and a communications or measurement and control peripheral.
The ENC10/12 is shipped with the 7363 enclosure supply kit that consists of desiccant, a humidity indicator card, cable ties, wire tie tabs, putty, grommets, screws, and PVC coupling. Additionally, Campbell Scientific offers a CS210 Enclosure Humidity Sensor for monitoring relative humidity inside of the enclosure. (See Ordering Info on the web page.)
|Color||White (Reflects solar radiation, reducing temperature gradients inside the enclosure without using a separate radiation shield.)|
|Construction||Fiberglass-reinforced polyester enclosure with door gasket, external grounding lug, stainless-steel hinge, and lockable hasps|
|Enclosure Classification||NEMA 4X (before being modified for cable entry)|
|Number of Cable-Entry Seals||1 medium, 2 small|
|Weight||4.1 kg (9.0 lb)|
Please note: The following shows notable compatibility information. It is not a comprehensive list of all compatible products.
|CR1000 (retired)||Although the CR1000 is compatible, this data logger can only fit inside the ENC10/12 if it is mounted vertically rather than horizontally.|
|CR3000 (retired)||The ENC10/12 is compatible with the CR3000 using the -NB option (base with no battery). Similar to the CR800/CR850 and CR1000, the CR3000 must be mounted vertically rather than horizontally. No space remains in the enclosure for additional peripherals.|
|CR800||Although the CR800 is compatible, this data logger can only fit inside the ENC10/12 if it is mounted vertically rather than horizontally.|
|CR850||Although the CR850 is compatible, this data logger can only fit inside the ENC10/12 if it is mounted vertically rather than horizontally.|
Retired peripherals that won’t fit in the same ENC10/12 enclosure as the data logger/power supply include the AVW4, AM416, COM100, CR10KD, DC1765, and RC35.
Number of FAQs related to ENC10/12: 12
Expand AllCollapse All
The following information is applicable to many of Campbell Scientific’s standard enclosures and prewired enclosures.
Note: The procedure below will not work for torn or damaged seals.
To make a field repair to a loose gasket on an enclosure, first acquire an adhesive, such as standard Gorilla Glue, that is rated for use with polyurethane foam. The adhesive should be compatible with, and recommended for, use with polyurethane foam. Follow these steps:
Yes. On the Ordering tab of the enclosure page on our website, scroll down to the Replacement Parts section. The Universal Backplate for the enclosure is listed there.
Backplates are available in sizes designed to fit in Campbell Scientific enclosures: 10 x 12 in., 12 x 14 in., 14 x 16 in., and 16 x 18 in.